John Dirks Jr Posted October 23, 2015 Report Share Posted October 23, 2015 I found a switched receptacle that tested as correct when the switch was in the on position and open neutral when the switch is turned off. To me it's obvious that the neutral conductor is connected to the switch instead of the hot conductor. It's wrong for sure but please describe to me a situation where this is a hazard. Quote Link to comment Share on other sites More sharing options...
Join the conversation
You can post now and register later. If you have an account, sign in now to post with your account.