palmettoinspect Posted June 2, 2017 Report Share Posted June 2, 2017 I'm kind of confused on this one and looking for some guidance. I've never seen this type of "Square D" disconnect used before. I could not get the cover to open to inspect, but it appears to feed the two 200 amp panels above and the small 60 amp panel above. My concern is two 200 amp panels are only fed with 3 wire feeders, not 4 wire and the ground and neutral wires are not separated. Given the big Square "D" box is a disconnect, shouldn't the two 200 amp panel be feed with 4 wire feeders and the ground and neutral separated? Thanks, Kiel Quote Link to comment Share on other sites More sharing options...
Join the conversation
You can post now and register later. If you have an account, sign in now to post with your account.