johnmcda Posted November 14, 2008 Report Share Posted November 14, 2008 Had a ground wire cut at the entrance to the panel on a 4 wire service. The panel did have a separate #6 copper ground. Should I be concerned? Image Insert: 180.48 KB Quote Link to comment Share on other sites More sharing options...
Join the conversation
You can post now and register later. If you have an account, sign in now to post with your account.