randynavarro Posted January 8, 2009 Report Share Posted January 8, 2009 This metal conduit feeds an A/C unit. It is not bonded to the panel nor is there a grounding conductor. Is this too-obviously incorrect or am I missing something? Click to View 64.95 KB Click to View 38.11 KB Quote Link to comment Share on other sites More sharing options...
Join the conversation
You can post now and register later. If you have an account, sign in now to post with your account.