John Dirks Jr Posted April 2, 2009 Report Share Posted April 2, 2009 The pictures show a splice in the main panel of 12NM to 1/0AL. The 1/0 AL then runs to a box on the air handler where it changes back to 12NM to feed power to the blower. Sparky is coming out for other reasons so I'll put a note in there for him to check this too. Meanwhile, help educate me. Is there anything specific that I should say is wrong with this arrangement? Click to Enlarge 53.77 KB Click to Enlarge 55.87 KB Quote Link to comment Share on other sites More sharing options...
Join the conversation
You can post now and register later. If you have an account, sign in now to post with your account.