Brandon Whitmore Posted May 11, 2007 Report Share Posted May 11, 2007 Just did an inspection for a one year warranty. Typical meter main installation with a distribution panel in the garage. The neutral and ground bus bars were not bonded together, but the neutral wires running off the AFCI breakers were attached to the ground bus bar. This seems like an improper installation to me, but was wired by an electrician and signed off by the city inspector. -- can anyone tell me whether or not this is allowed? Thanks Quote Link to comment Share on other sites More sharing options...
Join the conversation
You can post now and register later. If you have an account, sign in now to post with your account.