Robert Jones Posted April 16, 2010 Report Share Posted April 16, 2010 This really looks homeowner performed to me. Zinsco panel(called for replacement), There is a 50amp breaker installed(second breaker from the top) which services a sub panel in a detached garage. The feed wire from the home to the detached garage, appears to be 3 wire 2 gauge aluminum. I have not seen this size of feeder wire running to a detach before. Besides the fact it is low to the ground, is it the wrong size for a 50 amp breaker? Should it be a 4 wire feed? I hope the pics make some sense. Click to Enlarge 55.05 KB Click to Enlarge 59.17 KB Click to Enlarge 67.4 KB Click to Enlarge 56.72 KB Quote Link to comment Share on other sites More sharing options...
Join the conversation
You can post now and register later. If you have an account, sign in now to post with your account.