Rob Amaral Posted April 14, 2022 Report Share Posted April 14, 2022 Did a 2017-era inspection with an Eaton/Cutler-Hammer load-center this week (Apr 2022). Test-tripped the AFCIs and one 'sort of blew up' (arced, material spat out somewhat, etc). - I did not turn it back on, posted a note, made all the proper recommendations etc, but I'm not aware of this happening with any brand of breaker.... Thoughts?? I'm gonna go snooping-around the web for more info.. Quote Link to comment Share on other sites More sharing options...
Join the conversation
You can post now and register later. If you have an account, sign in now to post with your account.