Inspector Will Posted April 5, 2009 Report Share Posted April 5, 2009 I recently came across a sub-panel which appeared to be manufactured for a main panel use. A metal bar bonded the neutral and ground buses across the top of the panel. However, since it was utilized as a sub-panel the installer cut the bar that bonded the neutrals and grounds (see photos). It was clear that there was no alternate path that bonded the neutrals and grounds. Does anyone see a problem with this since there is no bond between the neutral and ground. Thanks for any feedback. Click to Enlarge 65.71 KB Click to Enlarge 56.15 KB Click to Enlarge 49.83 KB Quote Link to comment Share on other sites More sharing options...
Join the conversation
You can post now and register later. If you have an account, sign in now to post with your account.