Brandon Whitmore Posted January 28, 2010 Report Share Posted January 28, 2010 Today's house had a sub- panel in the crawlspace, with the service equip. panel in the garage above. The GEC ran to a ground rod in the crawlspace, so instead of running a 4 wire feed, a 3 wire feed (2 hots and neutral) was run to the sub- panel, and then a ground wire was tied into the GEC near the rod. The neutrals and grounds were separated in the panel. Is this a legit installation? I can't think of any reason why not, but I can't say I've run across it before. I've searched my house, and my code book is nowhere to be seen. I guess I should quit trying to organize things. Any help would be appreciated. Quote Link to comment Share on other sites More sharing options...
Join the conversation
You can post now and register later. If you have an account, sign in now to post with your account.