Neal Lewis Posted April 14, 2010 Report Share Posted April 14, 2010 I just want to confrim that this attic furnace draft hood spill switch is indeed intentionally bypassed. Both leads are connected (taped) to the left side terminal. Thanks Download Attachment: .jpg"] rsz_capone_012.jpg 93.39 KB Quote Link to comment Share on other sites More sharing options...
Join the conversation
You can post now and register later. If you have an account, sign in now to post with your account.