Rayne Posted May 12, 2020 Report Share Posted May 12, 2020 Square D QO main panel, my question is the only double pole breaker is 30 amp and so where is the main disconnect, and whats the amp rating on the panel. I see at the top of the panel it says the panel is rated for 100 amps so why would there not be a 100 amp disconnect? The only 240v circuit in the home is to the dryer everything else is gas. Is it possible they didn't install a main service disconnect because you could shut every circuit off with with 6 throws, which technically you couldn't because two of those are tandem breakers and I would think a tandem breaker would be two throws, any help would be much appreicated, thanks! Quote Link to comment Share on other sites More sharing options...
Join the conversation
You can post now and register later. If you have an account, sign in now to post with your account.