willf2900 Posted January 13, 2017 Report Share Posted January 13, 2017 The attached photo shows a Duke Energy underground service installation. The sweep exits grade 0ne foot from foundation and to the wall with 2 @45 degree fittings. The reason they said was due to the underground footing. I asked them to bury the sweep one foot lower and reinstall the 45 bends below grade. I think as presently installed it will be subject to physical damage from mowers and possibly vehicles since it is next to parking pad. Not sure if an expansion fitting is required by code either . Any help on this? Download Attachment: pvc lot 15.jpg 138.21 KB Click to Enlarge 84.57 KB Quote Link to comment Share on other sites More sharing options...
Join the conversation
You can post now and register later. If you have an account, sign in now to post with your account.