Trent Tarter Posted November 18, 2014 Report Share Posted November 18, 2014 I was talking with an experienced electrician today and would like some additional clarification. It was always my understanding that ground wires had to be separated from neutrals and bonded to panel in any remote distribution panels (aka sub panel). I was told by the electrician that it's only required when the downstream panel is located in the home, and that remote panels in any detached outbuilding do not require the grounds to be separated. The photo is a remote panel in detached garage, it's fed from the home's main service panel. Click to Enlarge 31.72 KB Click to Enlarge 52.58 KB Quote Link to comment Share on other sites More sharing options...
Join the conversation
You can post now and register later. If you have an account, sign in now to post with your account.