John Dirks Jr Posted November 9, 2015 Report Share Posted November 9, 2015 This 1" armored conduit was stuffed with at least 22 THHN conductors during a past panel upgrade. This will be a first for me writing up excessive conduit fill. You'd be hard pressed to fit another conductor in there. The conduit was at least 15' long passing through garage attic before disappearing into house attic. I'm pretty sure form past discussions on here that this is wrong so I'm writing it up. Do you concur? Click to Enlarge 45.73 KB Quote Link to comment Share on other sites More sharing options...
Join the conversation
You can post now and register later. If you have an account, sign in now to post with your account.