Robert Jones Posted April 18, 2010 Report Share Posted April 18, 2010 This service panel was added/updated in June 2009. Client called me to state that half of their home was without power and that there was sparks coming from the panel. They also stated that for the last week or so, that the lights in the home were flickering. This is the only location that I can find any signs of arcing. Would this be caused by the nut not being completely tightened? Click to Enlarge 51.19 KB Click to Enlarge 56.19 KB Quote Link to comment Share on other sites More sharing options...
Join the conversation
You can post now and register later. If you have an account, sign in now to post with your account.