Robert Jones Posted March 24, 2009 Report Share Posted March 24, 2009 The home I inspected today was built on 1998. 200amp service panel, copper branch wiring, panel is full. When I removed the cover I was quite surprised to find scorching to some of the neutrals. I am guessing that somewhere within the envelope of the home, there is an illegal jump of some sort that might lead to this? Overload? Feedback is greatly appreciated. Click to Enlarge 69.08 KB Click to Enlarge 54.04 KB Quote Link to comment Share on other sites More sharing options...
Join the conversation
You can post now and register later. If you have an account, sign in now to post with your account.