Richard Moore Posted November 25, 2009 Report Share Posted November 25, 2009 Well...this is new for me. My first residential 3-phase panel. Really a "sub" panel in a 1962 apartment fed from a 100-amp 3-phase service disconnect in the meter room. Nothing more than 2-pole breakers, of course, within the unit's panel. I'm going to report this as a 100-amp 3-phase 120-208 volt service even though, in reality, there is more than the usual 100-amps available. Would you describe it that way? Click to Enlarge 40.38 KB Click to Enlarge 99.86 KB Click to Enlarge 52.36 KB I also had a couple of double-tapped breakers, but this was my "favorite". Check out the connection of the blue wire. Almost got it! Click to Enlarge 40.73 KB Quote Link to comment Share on other sites More sharing options...
Join the conversation
You can post now and register later. If you have an account, sign in now to post with your account.