JohnC Posted April 1, 2010 Report Share Posted April 1, 2010 Hi, I have not seen this before in a panel. A Copper/Aluminum mix on a couple of breakers? Is this allowed? In addition the main disconnect is in the garage, so I told my client that the panel in the house is the sub panel and grounds and neutrals should be separated. The realtor told me I was wrong that "technically" the main disconnect is at the panel in the house. I really don't give a s--t about his thoughts and think he wrong, but I thought as I'm writing this report I would ask for input from the people whose opinion I do care about. John Callan Download Attachment: Aluminium & Copper.jpg 84.71 KB Download Attachment: Grounds and Neutals.jpg 109.26 KB Quote Link to comment Share on other sites More sharing options...
Join the conversation
You can post now and register later. If you have an account, sign in now to post with your account.