Chad Fabry Posted April 28, 2010 Report Share Posted April 28, 2010 Sorry, no pics, I'm not on my computer. 1965 Murray split bus 200 amp service. The panel has moderate rust from a leaking SE cable, a few of the mains have rust on the terminal screws and in the wire saddle, the phenolic cage is broken near where the se attaches and there are a handful of easily corrected wiring issues like double lugging, a defective GFCI breaker and a couple of aluminum wire branch circuits. I realize the NEC would require panel replacement for the rust issue or the broken cage issue but my client is a little concerned that suggesting panel replacement is over the top. I have two questions: Would your report suggest that the panel be replaced? If it was your panel, would you replace it? Quote Link to comment Share on other sites More sharing options...
Join the conversation
You can post now and register later. If you have an account, sign in now to post with your account.